How to set proper flow to your Eclipse Ozone Generator:
Connect the ﬂow meter provided to the “AIR IN” port on the base of the Eclipse.
Test the system by turning Eclipse system on.
SS Flow Meter Ball should be bouncing in middle.
If the Ball is stuck to either end, there is either too much or not enough flow.
After adjusting flow, remove Flow Meter and keep in safe spot.
How to adjust flow:
For Adjustable Injector Manifolds: gas ﬂow can be controlled by adjusting the valve on the Manifold. Close the valve to increase gas ﬂow; open the valve to decrease gas ﬂow.
For Rigid Injector Manifolds: this Manifold is equipped with a DELCheck spring loaded valve for automatic adjustment with a wide operating range. If more gas ﬂow is necessary, verify that other valves in the system are not inhibiting ﬂow through the Manifold.
If you experience complications see Trouble Shooting Section 4D in Eclipse Manual (see link below).